PROFINET is a mechanism to exchange data between controllers and devices. Controllers could be PLCs, DCSs, or PACs (Programmable Logic Controllers, Distributed Control Systems, or Programmable Automation Controllers.). Devices could be I/O blocks, vision systems, RFID readers, drives, process instruments, proxies, or even other controllers. Fast and Deterministic PROFINET exchanges data quickly and deterministically. Required speeds vary depending on the […]
PROFINET is great at moving information across a network – we never get tired hammering that message home. But exactly how PROFINET moves that information is still a gray area for a lot of users, and deserves a closer look here. To understand how PROFINET moves information, it helps to keep in mind what kind of information it’s moving. Does […]
A PROFINET network can be a complex collection of stations, from digital I/O devices to pneumatic actuators to laser scanners… the list seems endless and grows every day. But within that complex network, all PROFINET components operate within three different roles. They can be either Devices, Controllers, or Supervisors.
In our article on PROFINET Components, we saw that most of the communication in PROFINET flows between Devices and Controllers. Supervisors don’t get much attention because they don’t get involved in production work. However, a PROFINET Supervisor can be a great tool during system commissioning, checkout, and even to troubleshoot when there’s a problem. PROFINET supervisors operate in a similar […]
At its heart, PROFINET is based on standard Ethernet IEEE 802.3 Physical layers using 802.3 supporting components. PROFINET will work on copper Ethernet cable, Fiber Optical (FO) cable, Power Over Ethernet (PoE) cable and Wireless. The components available for your PROFINET infrastructure depend on the harshness of the environment and whether or not you are using PROFINET IRT. PROFINET Infrastructure PROFINET […]
PROFINET offers a massive breadth and depth of application scenarios for industrial automation. Examples of breadth include wired and wireless IO, factory automation, motion control with IRT for drives/motors, and process automation. Examples of depth include simple device replacement/commissioning, fast startup, Shared and I -device, and redundancy, just to name a few. If you have questions about application criteria, for example about network topology, commissioning devices, […]
Prior to starting your next PROFINET project, we recommend that you take a close look at PI’s PROFINET installation guidelines and planning tools. These guidelines were designed by engineers for engineers. They will help you with the design, installation, and commissioning of your PROFINET system. They contain tips and specifics that are often overlooked. There are three main guides a design guideline, an […]
What is a GSD File? A PROFINET General Station Description (GSD) file is a description of an IO device provided by the device manufacturer. The contents of the GSD consists of configuration information, parameters, modules, diagnostic and alarms, and vendor and device identification. To discuss the latter two in a little more detail, the vendor identification (vendor ID) is a number […]
PROFINET has class, in fact, many classes: Conformance Classes, Real Time classes, media redundancy classes, and even more class(es). This article covers Real Time Classes and how PROFINET works.
It should come as no surprise that PROFINET also supports motion control applications with drives and motors (sometimes also referred to as VFDs – Variable Frequency Drives) as these are used in most modern automation systems. Motion control support comes with PROFINET technology from three main aspects: 1.) The ability for scalable real-time control depending on the drive application 2.) […]
When you mention the words “real-time” and “Ethernet” in the same sentence, let alone next to each other, you get some incredulous looks. Ethernet, by definition, is an open network that allows anyone to transmit at any time – making it a probabilistic transmission medium. Unless there’s abnormally high bandwidth utilization, Ethernet is built on the assumption that nodes will probably […]
PROFINET DCP is part of the protocol suite and stands for “Discovery and basic Configuration Protocol”. It is used by the engineering tool and controller to discover devices, identify device information, and configure device settings such as PROFINET device name and IP address on a PROFINET network.